SkanDek - GreenLine Brand
SkanDek roof panels are unique when it comes to fire retardant roofing systems. SkanDekâ€™s panels inhibit the spread of fire since the supporting materials in the panels are non-flammable and fire inhibiting
Even without fire protection Skandekâ€™s panels, with a steel-trapeze plate on the ceiling, can achieve fire resistance of up to 30 minutes. If the ceiling side is covered with rigid insulation or gypsum boards, the SkanDek plates can achieve fire resistance of up to 60 minutes.
Steel-roof panels with mineral wool fitted between spaced wooden boarding can achieve fire resistance of up to 60 minutes, if two layers of plaster or one layer of 25 mm concrete wood is retro-fitted on the underside of the roof construction
Combustible enclosure replacement
Avoid dangerous combustible enclosures on the roof by having the SkanDek panels made as REI 60 (see extent and fire classes in the link to SBI directions below).
Avoid class 1 covering of steel-trapeze plates over suspended ceilings
Since the supporting parts of the steel-roof box structure are considered non-flammable, class 1 covering under the steel-trapeze plates is not necessary if these are to function as underlay for suspended ceilings (see fire retardant valuations below).
Fire resistance valuation and blueprints
- Drawings of ceiling and roof covering, as well as their functional requirements.
- REI 30 / BD-30: Ceiling with spacing boards and gypsum boards.
- REI 30 / BS-30: Ceiling with steel-trapeze plates.
- REI 60 / BS-60: Ceiling made of 20 mm rigid Rockwool with a perforated steel-trapeze plate under 1).
- REI 60 / BS-60: Ceiling with steel-trapeze plates covered with fireproof plaster board 1).
- REI 60 / BD-60: Mineral wool fitted between spacing boards, covered C.I.P with either plaster or concrete wood plates.
- REI 60 / BS-60: 20 mm rigid insulation fitted with wind shield taping per. 400 mm to overlying steel-trapeze plate.
- Steel trapeze plate as class 1 covering on ceiling.
Annexes and links re. Combustible enclosures and thin-plate constructions
- SkanDek elements have been testet by DBI, Danish Institute of Fire and Security Technology. The tests are performed to international and Danish fire test standards, published, amongst others, by CEN, DS, IMO, ISO and Nordtest – most of them as accredited tests. DBI is accredited by DANAK, the national accreditation body in Denmark.
- SBI Direction, Section 5.5.2 re, combustible chamber substitution fire and smoke spread.
- Note; Steel trapeze roofing, fire. Thin metal plating June 2007.
- When designing smoke ventilation, please refer to DS 428, and the Danish Enterprise and Construction Authority.
1)The reason why the BS-60 fire retardant valuation does not agree with the new REI 60 A2-s1,d0, is that the test methods and material classifications are not the same as in the previous national requirements to achieve material classification A.
Synlige eller nedhængte lofter.
Isoleringspladen vil være fastholdt af en trapezplade, som enten kan leveres perforeret til synlige lofter, eller u-perforeret til nedhængte lofter.
Da de bærende dele af elementet kan anses for, at være ubrandbare, kan man spare eftermonteringe af klasse 1 beklædning under ståltrapezpladerne, hvis disse skal fungere som underlag for nedstroppede lofter (se brandbedømmelse).
Brandkravet sammenholdt med de to typer trapezplader giver tilsammen fire forskellige loftkombinationer for SkanDek GreenLine.
- 30 min – Loft med 20 mm trykfast isolering og 18 mm u-perforeret ståltrapezplade
- 30 min – Loft med 20 mm trykfast isolering og 18 mm perforeret ståltrapezplade(synligt loft)
- 60 min – Loft med 40 mm trykfast isolering og 18 mm u-perforeret ståltrapezplade
- 60 min – Loft med 40 mm trykfast isolering og 18 mm perforeret ståltrapezplade(synligt loft)